Three-way switches allow for controlling a light fixture from two separate locations, these are usually used at the top and bottom of a flight of stairs or at two different entrances to a room. On this page are several wiring diagrams that can be used to map 3 way lighting circuits depending on the location of the source with relation to the lights.
This diagram is the same as the one above but the dimmer comes first in the circuit. This arrangement is provided for easy reference when dealing with a circuit wired like this.
This page contains wiring diagrams for most household receptacle you will encounter including grounded and ungrounded duplex outlets, ground fault circuit interrupters (GFCI) as well as 20amp, 30amp and 50amp receptacles for 120 volt and 240 volt circuits.
This diagram illustrates the wiring for a split receptacle with the top half controlled by SW1 and the bottom half always hot. The receptacle is split by breaking the connecting tab between the two, brass colored terminals. The tab between the neutral, silver terminals should remain intact.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.