Here again, the connecting tab between the receptacle terminals is broken off and the neutral tab remains intact. The source is at SW1 and 3-conductor cable runs from there to the receptacle, 2-conductor cable runs from the receptacle to SW2. The source hot wire is spliced to the bottom terminal on SW1 and to the red cable running to the receptacle.
This page contains wiring diagrams for most household receptacle you will encounter including grounded and ungrounded duplex outlets, ground fault circuit interrupters (GFCI) as well as 20amp, 30amp and 50amp receptacles for 120 volt and 240 volt circuits.
A combo switch/receptacle is handy when you need both, but you only have one outlet box available. Like the split receptacles above these devices makes use of a removable connector between the two, hot terminals to divide the device when needed. When intact and wired to one hot source wire, the combo device can be used to turn a light off and on, while the receptacle will be constantly hot.
To wire this circuit, 2-conductor cable runs from the dimmer to the light. The source is at the dimmer and the hot wire is spliced to one hot wire on the device. The other wire from the dimmer is spliced to the black cable wire which runs on to the hot terminal on the light. The source neutral wire is spliced to the white cable wire which continues on to the neutral terminal on the light.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.