Here the source is at the receptacle and 2-conductor cable runs from there to SW1. The hot source is spliced to a pigtail that connect to the bottom, always-hot, half on the receptacle and to the white cable wire which continues on to the bottom terminal on SW1. The black cable wire is connected to the top terminal on the split receptacle and runs to the top terminal on SW1. The circuit neutral wire is connected to one of the neutral terminals on the receptacle, it doesn’t run to the switch.
This diagram shows the wiring to control a receptacle outlet with two 3 way switches. The source is at SW1 and 3-wire cable runs between all the devices. The hot wire from the source connects to the common terminal on SW1. The common on SW2 is connected to the hot terminal on the receptacle. The traveler wires are spliced in the receptacle box to run to the traveler terminals on each switch. The white cable wire is used as a traveler to SW2 and marked hot with black tape.
The diagrams on this page illustrate connecting multiple lights in 3 way and 4 way switch circuits. Check below for more details about these circuits and some troubleshooting tips.
The wiring diagrams on this page make use of 4 way switches, between two 3 way switches, to control lights from three or more locations. A 4-way dimmer diagram is included as well as an arrangement to control the lights from four different points. Check here for 4 way switch troubleshooting and help with 3 ways switches here. For circuits that control lights from two locations only, check the wiring diagrams at this link.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.