In this arrangement two 3-way dimmers are used to allow for lowering the lights from both locations. Here the common on the first dimmer connects to the hot source and the common on the second connects to the hot on the light. As with all these types of circuits the traveler wires run between the switches and connect the traveler terminals.
Here two 4 way and two 3 way switches are used to control lights from four different locations. The source is at SW1 and the hot wire is connected to the common terminal. Three-wire cable runs between all switches and 2-wire cable runs from the last switch to the light fixture. The light hot connects to the common terminal on SW2.
Here a single-pole switch controls the electricity to a light fixture. The source is at the switch and 2-conductor cable runs from there to the light. The source hot wire is connected to the bottom terminal on the switch and the top terminal is connected to the black cable wire. The neutral wire from the source is spliced to the white cable wire and continues on to the light. At the light, the white wire connects to the neutral terminal and the black wire connects to the hot.
Included is a diagram for a 3 way dimmer and an arrangement to control a receptacle from two locations. For more information about these circuits and troubleshooting tips check below.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.