Here a receptacle outlet is controlled with a single-pole switch. This is commonly used to turn a table lamp on and off when entering a room. In this diagram, 2-conductor cable runs between SW1 and the outlet. The source is at SW1 and the hot wire is connected to the bottom terminal there. The top terminal is connected to the black cable wire running to the hot terminal on the receptacle and the source neutral is spliced with the white cable wire which runs on to the neutral on the receptacle.
In this circuit, two fixtures are shown but more can be added by duplicating the wiring arrangement between the lights for each one added. Here the source is at SW1 and 3-wire cable runs from there to L1. Two, 2-wire cables run between the fixtures, and 3-wire cable runs from the last one to SW2.
This diagram illustrates wiring for a 4 way circuit with the electrical source at the light fixture and the switches coming after. Two-wire cable is run from the light to SW1 and 3-wire cable runs between all the switches. The hot source is spliced through to the common terminal on SW2 and the hot terminal on the light fixture is connected to the common on SW1. The travelers run from SW1 to T1 on the 4 way and from T2 to the travelers on SW2. Note that the white wire is wrapped with black electrical tape when it is used for hot in these circuits.
This wiring diagram is used for 50 and 60 amp circuits. The receptacle should be wired to a dedicated 50 or 60 amp circuit breaker using 6 awg cable. The 50 amp circuit is required for new installations of some large appliances requiring 240 volts. Two wires carrying 120 volts each can be combined to provide high voltage to heating circuits and one of the 120 volt wires can serve lights or other low voltage circuits in the appliance.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.