This is an older version of the receptacle in the first diagram. The slots are different sizes to accept polarized plugs, but it lacks a grounding slot. This device does not make use of a ground wire. There is no protection against electrocution as provide by the grounded receptacle.
When replacing an ungrounded, polarized receptacle use this type and not the grounded type above, unless it is grounded by a jumper wire to a metal outlet box that is tied to the house service panel ground through a continuos metal conduit.
This diagram illustrates wiring for a 4 way circuit with the electrical source at the light fixture and the switches coming after. Two-wire cable is run from the light to SW1 and 3-wire cable runs between all the switches. The hot source is spliced through to the common terminal on SW2 and the hot terminal on the light fixture is connected to the common on SW1. The travelers run from SW1 to T1 on the 4 way and from T2 to the travelers on SW2. Note that the white wire is wrapped with black electrical tape when it is used for hot in these circuits.
If your switches stop working they may be worn out or the screws may have come loose. If you’ve wired a new switch correctly and the circuit still doesn’t work, the switch may be defective. Check that all connections are tight. Check the switch, remove it from the circuit and test for failure with a continuity tester or multimeter set on the Ohms setting.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.