This is an older version of the receptacle in the first diagram. The slots are different sizes to accept polarized plugs, but it lacks a grounding slot. This device does not make use of a ground wire. There is no protection against electrocution as provide by the grounded receptacle.
To wire this circuit, 2-conductor cable runs from the dimmer to the light. The source is at the dimmer and the hot wire is spliced to one hot wire on the device. The other wire from the dimmer is spliced to the black cable wire which runs on to the hot terminal on the light. The source neutral wire is spliced to the white cable wire which continues on to the neutral terminal on the light.
Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
In this circuit a split receptacle is controlled by two separate switches. With this arrangement two lamps can be plugged into the same receptacle and each can be controlled separately from two different locations.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.