A 4 way switch must be wired between two 3 ways as shown in the diagrams on this page. A 4 way has five connections: one ground, and 4 circuit terminals divided into two matching pairs. Each pair of terminals should be wired to the traveler wires from one of the 3 way switches. The travelers can be wired to either terminal in a pair, but don’t mix up the pairs or the circuit won’t work properly.
Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be connected to the switches in these circuits, although some smart switches may make use of a neutral wire to operate the device.
In this updated diagram 3-conductor cable runs between the receptacle and switch, and the red cable wire is used to carry the hot source to the bottom terminal on the switch. The neutral from the source is passed through to the switch box using the white wire and in this diagram the white wire is capped with a wire nut.
When using this device for heavy appliances like washing machines and microwaves, it should be connected to a dedicated 20-amp/120-volt circuit breaker. As of 2014, a GFCI receptacle is now required in a laundry room for the washing machine.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.