Here a receptacle is added to the circuit before the first switch. It is not controlled with the switches but is instead always hot. The source hot, neutral and ground are spliced to a 2-wire cable that runs to the new outlet. The 3 way switches and light are then wired in the usual way with the common on SW2 spliced to the source hot and the light hot wired to the common on SW1.
Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be connected to the switches in these circuits, although some smart switches may make use of a neutral wire to operate the device.
This diagram illustrates the wiring for a split receptacle with the top half controlled by SW1 and the bottom half always hot. The receptacle is split by breaking the connecting tab between the two, brass colored terminals. The tab between the neutral, silver terminals should remain intact.
This is the oldest version of a wall receptacle that you will find. It lacks a grounding contact and the plug slots are both the same size. These devices did not make use of a ground wire and both plug slots were treated the same. The wires used with these receptacles were usually both black.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.