In this arrangement two 3-way dimmers are used to allow for lowering the lights from both locations. Here the common on the first dimmer connects to the hot source and the common on the second connects to the hot on the light. As with all these types of circuits the traveler wires run between the switches and connect the traveler terminals.
In this updated diagram 3-conductor cable runs between the receptacle and switch, and the red cable wire is used to carry the hot source to the bottom terminal on the switch. The neutral from the source is passed through to the switch box using the white wire and in this diagram the white wire is capped with a wire nut.
Check to be sure the traveler wires only connect between the traveler terminals on the switches. Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be used with these switches, although some smart switches may make use of a neutral wire to operate the device.
The traveler terminals will always be connected from switch to switch. Travelers never connect to a device load or to a source wire. It doesn’t matter which traveler terminal is used for which traveler wire, reversing them should make no difference.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.