Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
If your switches stop working they may be worn out or the screws may have come loose. If you’ve wired a new switch correctly and the circuit still doesn’t work, the switch may be defective. Check that all connections are tight. Check the switch, remove it from the circuit and test for failure with a continuity tester or multimeter set on the Ohms setting.
This is an older version of the receptacle in the first diagram. The slots are different sizes to accept polarized plugs, but it lacks a grounding slot. This device does not make use of a ground wire. There is no protection against electrocution as provide by the grounded receptacle.
In this diagram the electrical source is at the first switch and the light is located at the end of the circuit. Three-wire cable runs between the switches and 2-wire cable runs to the light. The black and red wires between SW1 and SW2 are connected to the traveler terminals. The hot source is connected to the common terminal on SW1, and the common terminal on SW2 connects to the hot terminal on the light.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.