Here again, the connecting tab between the receptacle terminals is broken off and the neutral tab remains intact. The source is at SW1 and 3-conductor cable runs from there to the receptacle, 2-conductor cable runs from the receptacle to SW2. The source hot wire is spliced to the bottom terminal on SW1 and to the red cable running to the receptacle.
Here the source is at the receptacle and 2-conductor cable runs from there to SW1. The hot source is spliced to a pigtail that connect to the bottom, always-hot, half on the receptacle and to the white cable wire which continues on to the bottom terminal on SW1. The black cable wire is connected to the top terminal on the split receptacle and runs to the top terminal on SW1. The circuit neutral wire is connected to one of the neutral terminals on the receptacle, it doesn’t run to the switch.
The 4 way comes right after the light fixture, but before the second 3 way switch, making it fall between the two 3 ways as needed. It could also be installed on the other side of the light and the effect would be the same.
This receptacle can typically be found in living room and bedroom wall outlets. One of these may be controlled with a switch and/or wired to other receptacles in the circuit. For a 15 amp receptacle like this, 14/2 cable with ground should be used to feed the circuit.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.