In this circuit, two fixtures are shown but more can be added by duplicating the wiring arrangement between the lights for each one added. Here the source is at SW1 and 3-wire cable runs from there to L1. Two, 2-wire cables run between the fixtures, and 3-wire cable runs from the last one to SW2.
This diagram illustrates wiring for a 4 way circuit with the electrical source at the light fixture and the switches coming after. Two-wire cable is run from the light to SW1 and 3-wire cable runs between all the switches. The hot source is spliced through to the common terminal on SW2 and the hot terminal on the light fixture is connected to the common on SW1. The travelers run from SW1 to T1 on the 4 way and from T2 to the travelers on SW2. Note that the white wire is wrapped with black electrical tape when it is used for hot in these circuits.
This page contains wiring diagrams for household light switches and includes a switch loop, single-pole switches, light dimmer, and a few choices for wiring a combo switch/outlet device. Also included are wiring arrangements for multiple light fixtures controlled by one switch, and a split receptacle controlled by two switches.
A 20 amp, 120v duplex receptacle like this should be installed in a circuit using 12 awg or larger cable and a 20 amp circuit breaker. These receptacles are usually found in kitchen wall outlets where two branch circuits are needed to serve small appliances and a refrigerator.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.