This wiring shows the light fixture and the electrical source between the switches. Three-wire cable runs throughout and the hot source is splice to the common on SW1. The common on SW2 is spliced through to the hot on the light fixture. The travelers from SW1 are spliced at the fixture outlet box to run to the 4 way switch.
At the beginning of the circuit the hot source is connected to the common terminal on SW1. The neutral is spliced to the white cable wire and then spliced to the neutral terminal at L1, along with the white 2-cable wire running to L2 where it connects to the neutral terminal.
In this circuit, two fixtures are shown but more can be added by duplicating the wiring arrangement between the lights for each one added. Here the source is at SW1 and 3-wire cable runs from there to L1. Two, 2-wire cables run between the fixtures, and 3-wire cable runs from the last one to SW2.
The following 3 diagrams show the wiring for a specially made dimmer that can be used in these circuits in place of either of the the 3 way switches, or both. This arrangement allows for lowering the lights in a 3 way circuit. After the dimmer level has been set the other switch will turn the lights off and on at that level. This device can be used in place of any of the 3 way switches in these circuits, as well as to dim the lights in a 4 way circuit.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.