The source in this circuit is at the first switch and the light fixture is located between SW1 and SW2. Three-wire cable runs between each switch and the light fixture. The hot source wire is connected to the common terminal on SW1. The common terminal on SW2 is connected to the hot terminal on the light. The traveler wires are spliced at the fixture box to run between the traveler terminals on the switches.
The 4 way comes right after the light fixture, but before the second 3 way switch, making it fall between the two 3 ways as needed. It could also be installed on the other side of the light and the effect would be the same.
This page contains wiring diagrams for household light switches and includes a switch loop, single-pole switches, light dimmer, and a few choices for wiring a combo switch/outlet device. Also included are wiring arrangements for multiple light fixtures controlled by one switch, and a split receptacle controlled by two switches.
This is an updated version of the first arrangement. Because the electrical code as of the 2011 NEC update requires a neutral wire in most new switch boxes, a 3-wire cable runs between the light and switch. The red and black are used for hot and the white neutral wire at the switch box allows for powering a remote controlled switch.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.