Here a receptacle is added to the circuit before the first switch. It is not controlled with the switches but is instead always hot. The source hot, neutral and ground are spliced to a 2-wire cable that runs to the new outlet. The 3 way switches and light are then wired in the usual way with the common on SW2 spliced to the source hot and the light hot wired to the common on SW1.
This diagram illustrates another multiple light circuit controlled by 3 way switches. Here the source and the fixtures come before the switches. As with the other diagrams on this page, more lights can be added by duplicating the arrangement between the fixtures.
The 4 way comes right after the light fixture, but before the second 3 way switch, making it fall between the two 3 ways as needed. It could also be installed on the other side of the light and the effect would be the same.
There are two sets of terminals on a ground fault circuit interrupter (gfci) receptacle: the line terminals and the load terminals. The source from the circuit should be connected to the line terminals and any standard duplex outlet or other device connected to the load terminals will be protected by this gfci.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.