Included is a diagram for a 3 way dimmer and an arrangement to control a receptacle from two locations. For more information about these circuits and troubleshooting tips check below.
When using this device for heavy appliances like washing machines and microwaves, it should be connected to a dedicated 20-amp/120-volt circuit breaker. As of 2014, a GFCI receptacle is now required in a laundry room for the washing machine.
Here two switches are wired in the same box to control two separate lights. The source is at the switch box and a 2-conductor cable is run to each light. One source is spliced to each switch with a pigtail to power the two lights.
Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be connected to the switches in these circuits, although some smart switches may make use of a neutral wire to operate the device.
A 20 amp, 120v duplex receptacle like this should be installed in a circuit using 12 awg or larger cable and a 20 amp circuit breaker. These receptacles are usually found in kitchen wall outlets where two branch circuits are needed to serve small appliances and a refrigerator.
Here a single-pole switch controls the electricity to a light fixture. The source is at the switch and 2-conductor cable runs from there to the light. The source hot wire is connected to the bottom terminal on the switch and the top terminal is connected to the black cable wire. The neutral wire from the source is spliced to the white cable wire and continues on to the light. At the light, the white wire connects to the neutral terminal and the black wire connects to the hot.
In order for a 4 way circuit to work, the 3 way switches must be wired properly at the the beginning and end of the path. So be sure that the common terminal on one of the 3 ways is wired to the hot source, and the common on the second 3 way is wired to the the hot terminal on the lights.
This outlet is commonly used for a heavy load such as a large air conditioner. The outlet should be wired to a dedicated 20-amp/240-volt circuit breaker in the service panel using 12|2 awg cable.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.