This diagram illustrates another multiple light circuit controlled by 3 way switches. Here the source and the fixtures come before the switches. As with the other diagrams on this page, more lights can be added by duplicating the arrangement between the fixtures.
When replacing an ungrounded, polarized receptacle use this type and not the grounded type above, unless it is grounded by a jumper wire to a metal outlet box that is tied to the house service panel ground through a continuos metal conduit.
Included is a diagram for a 3 way dimmer and an arrangement to control a receptacle from two locations. For more information about these circuits and troubleshooting tips check below.
When the electrical source originates at a light fixture and it’s controlled from a remote location, a switch loop is used. The circuit pictured here is wired with 2-conductor cable running from the light to the switch location. The white cable wire in this switch loop is wrapped with black tape and connected to the bottom terminal on SW1 and the hot source at the light. The black wire is connected to the top terminal on SW1 and the hot terminal on the light fixture. The neutral from the source is connected directly to the neutral terminal on the light.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.