This drawing shows the wiring for multiple lights in a 4 way circuit with the source and fixtures coming before the switches. More lights can be added to this circuit by duplicating the wiring shown here for each additional fixture. Here 3-wire cable runs between L1 and L2, 2-wire cable runs from the last fixture to SW1, and 3-wires runs between SW1 and SW2.
Here two switches are wired in the same box to control two separate lights. The source is at the switch box and a 2-conductor cable is run to each light. One source is spliced to each switch with a pigtail to power the two lights.
The source in this circuit is at the first switch and the light fixture is located between SW1 and SW2. Three-wire cable runs between each switch and the light fixture. The hot source wire is connected to the common terminal on SW1. The common terminal on SW2 is connected to the hot terminal on the light. The traveler wires are spliced at the fixture box to run between the traveler terminals on the switches.
Here two 4 way and two 3 way switches are used to control lights from four different locations. The source is at SW1 and the hot wire is connected to the common terminal. Three-wire cable runs between all switches and 2-wire cable runs from the last switch to the light fixture. The light hot connects to the common terminal on SW2.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.