Check to be sure the traveler wires only connect between the traveler terminals on the switches. Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be used with these switches, although some smart switches may make use of a neutral wire to operate the device.
Here two switches are wired in the same box to control two separate lights. The source is at the switch box and a 2-conductor cable is run to each light. One source is spliced to each switch with a pigtail to power the two lights.
The two 4-ways are located between the two 3-ways and the traveler wires run from SW1 to T1 on the first 4-way. T2 from that switch is wired to T1 on the second 4way and the output from there to the traveler terminals on SW2.
The following 3 diagrams show the wiring for a specially made dimmer that can be used in these circuits in place of either of the the 3 way switches, or both. This arrangement allows for lowering the lights in a 3 way circuit. After the dimmer level has been set the other switch will turn the lights off and on at that level. This device can be used in place of any of the 3 way switches in these circuits, as well as to dim the lights in a 4 way circuit.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.