At the beginning of the circuit the hot source is connected to the common terminal on SW1. The neutral is spliced to the white cable wire and then spliced to the neutral terminal at L1, along with the white 2-cable wire running to L2 where it connects to the neutral terminal.
This drawing shows the wiring for multiple lights in a 4 way circuit with the source and fixtures coming before the switches. More lights can be added to this circuit by duplicating the wiring shown here for each additional fixture. Here 3-wire cable runs between L1 and L2, 2-wire cable runs from the last fixture to SW1, and 3-wires runs between SW1 and SW2.
This represents a change in the NEC code that requires a neutral wire in most new switch boxes. If you are running a new circuit check the electrical code to understand this and any other updates to the required procedure.
A rheostat, or dimmer, makes it possible to vary the current flowing to a light fixture thereby varying the intensity of the light. The dimmer switch will have stranded wires that must be sliced to the solid cable wiring with a pigtail. A device like this should only be used with an incandescent light fixture and not with a ceiling fan or other motor. See wiring a speed controller for wiring a rheostat to control fan speed.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.