In order for a 4 way circuit to work, the 3 way switches must be wired properly at the the beginning and end of the path. So be sure that the common terminal on one of the 3 ways is wired to the hot source, and the common on the second 3 way is wired to the the hot terminal on the lights.
In this diagram the electrical source is at the first switch and the light is located at the end of the circuit. Three-wire cable runs between the switches and 2-wire cable runs to the light. The black and red wires between SW1 and SW2 are connected to the traveler terminals. The hot source is connected to the common terminal on SW1, and the common terminal on SW2 connects to the hot terminal on the light.
The traveler wires are run using the other 2-wire cable between the lights and continue on to the traveler terminals on SW2. They don’t connect to the fixtures at all.
This receptacle can typically be found in living room and bedroom wall outlets. One of these may be controlled with a switch and/or wired to other receptacles in the circuit. For a 15 amp receptacle like this, 14/2 cable with ground should be used to feed the circuit.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.