Here two switches are wired in the same box to control two separate lights. The source is at the switch box and a 2-conductor cable is run to each light. One source is spliced to each switch with a pigtail to power the two lights.
In this diagram the source for the circuit is at the light fixture and the two switches come after. Two-wire cable runs from the light, to SW1 and 3-wire cable runs between SW1 and SW2. The hot source is spliced to the white cable-wire, which is wrapped with black tape to mark it as hot and run through to SW1 where it is spliced to the black wire running to the common terminal on SW2. The hot terminal on the light fixture is connected to the common terminal on SW1. The red wire and marked white wire travelers connect the traveler terminals between the two switches.
In this updated diagram 3-wire cable runs between the receptacle and SW2 to allow for splicing the neutral source through to the second switch box. Here the white is not used for hot but instead the extra, red wire serves that purpose for the second switch.
When replacing an ungrounded, polarized receptacle use this type and not the grounded type above, unless it is grounded by a jumper wire to a metal outlet box that is tied to the house service panel ground through a continuos metal conduit.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.