At the receptacle the black cable wire from SW1 is connected to one of the hot terminals and the red wire is spliced to the white wire on the 2-conductor cable running to SW2. The white wire is wrapped with electrical tape to mark it as hot. The black wire is connected to the second hot terminal on the receptacle and to the top terminal on SW2 at the other end.
To wire more than one GFCI receptacle in the same circuit, connect the source to the line terminals on each device using a pigtail splice. The load terminals are not used for this circuit. See more GFCI wiring diagrams at this link.
This wiring diagram is used for 50 and 60 amp circuits. The receptacle should be wired to a dedicated 50 or 60 amp circuit breaker using 6 awg cable. The 50 amp circuit is required for new installations of some large appliances requiring 240 volts. Two wires carrying 120 volts each can be combined to provide high voltage to heating circuits and one of the 120 volt wires can serve lights or other low voltage circuits in the appliance.
Depending on the manufacturer, the travelers may be on opposite sides of the device or the two terminals may be on the same side. In any case, the common terminal will be distinguished from the travelers in some way.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.