This is another option for wiring a combo device where two sources are used. In this arrangement the connecting tab between the hot terminals on the device is broken off to separate the two. The switch controls a light and the receptacle half of the combo device is always hot.
In a kitchen where only one outlet box is available and both a switch for a garbage disposal and a gfci receptacle are needed, a a switch/gfci combo can be used as in the diagram at this link.
This is the wiring for a dimmer in a 4 way circuit. To make this circuit work, a 3 way dimmer is used in place of one or both of the standard 3 way switches. A dimmer can be added in this way to any of the circuits on this page. A 3 way dimmer has 4 wires: one common, two travelers and a ground.
In order for a 4 way circuit to work, the 3 way switches must be wired properly at the the beginning and end of the path. So be sure that the common terminal on one of the 3 ways is wired to the hot source, and the common on the second 3 way is wired to the the hot terminal on the lights.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.