In this arrangement two 3-way dimmers are used to allow for lowering the lights from both locations. Here the common on the first dimmer connects to the hot source and the common on the second connects to the hot on the light. As with all these types of circuits the traveler wires run between the switches and connect the traveler terminals.
This receptacle can typically be found in living room and bedroom wall outlets. One of these may be controlled with a switch and/or wired to other receptacles in the circuit. For a 15 amp receptacle like this, 14/2 cable with ground should be used to feed the circuit.
The top terminal is connected to the black cable wire, and the source neutral is spliced to the white wire which continues on to one of the neutral terminals on the receptacle, it doesn’t matter which, only one connection is needed with the neutral wire.
This diagram shows the wiring to control a receptacle outlet with two 3 way switches. The source is at SW1 and 3-wire cable runs between all the devices. The hot wire from the source connects to the common terminal on SW1. The common on SW2 is connected to the hot terminal on the receptacle. The traveler wires are spliced in the receptacle box to run to the traveler terminals on each switch. The white cable wire is used as a traveler to SW2 and marked hot with black tape.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.