The top terminal is connected to the black cable wire, and the source neutral is spliced to the white wire which continues on to one of the neutral terminals on the receptacle, it doesn’t matter which, only one connection is needed with the neutral wire.
At the receptacle the black cable wire from SW1 is connected to one of the hot terminals and the red wire is spliced to the white wire on the 2-conductor cable running to SW2. The white wire is wrapped with electrical tape to mark it as hot. The black wire is connected to the second hot terminal on the receptacle and to the top terminal on SW2 at the other end.
Back at the lights the source neutral is connected to the neutral terminal on L1 and spliced with the white wire running between the fixtures. At each light it’s connected to the neutral terminal. At SW1 the red and white wires from the 3-wire cable running between switches function as the travelers with the white marked for hot using black tape or paint.
This is an updated version of the first arrangement. Because the electrical code as of the 2011 NEC update requires a neutral wire in most new switch boxes, a 3-wire cable runs between the light and switch. The red and black are used for hot and the white neutral wire at the switch box allows for powering a remote controlled switch.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.