Back at the lights the source neutral is connected to the neutral terminal on L1 and spliced with the white wire running between the fixtures. At each light it’s connected to the neutral terminal. At SW1 the red and white wires from the 3-wire cable running between switches function as the travelers with the white marked for hot using black tape or paint.
The 4 way comes right after the light fixture, but before the second 3 way switch, making it fall between the two 3 ways as needed. It could also be installed on the other side of the light and the effect would be the same.
At SW1 the white wire is wrapped with black tape and run through to the common on SW2 using the white wire at each switch. At the lights the white wire from SW2 is spliced to the hot terminal on each fixture. The black and red wires running between the switches serve as the travelers for the circuit. At the 4 way the travelers from SW1 connect to T1 and T2 connect to the travelers for SW2.
If your switches stop working they may be worn out or the screws may have come loose. If you’ve wired a new switch correctly and the circuit still doesn’t work, the switch may be defective. Check that all connections are tight. Check the switch, remove it from the circuit and test for failure with a continuity tester or multimeter set on the Ohms setting.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.