The top terminal is connected to the black cable wire, and the source neutral is spliced to the white wire which continues on to one of the neutral terminals on the receptacle, it doesn’t matter which, only one connection is needed with the neutral wire.
A 4 way switch must be wired between two 3 ways as shown in the diagrams on this page. A 4 way has five connections: one ground, and 4 circuit terminals divided into two matching pairs. Each pair of terminals should be wired to the traveler wires from one of the 3 way switches. The travelers can be wired to either terminal in a pair, but don’t mix up the pairs or the circuit won’t work properly.
This diagram is the same as the one above but the dimmer comes first in the circuit. This arrangement is provided for easy reference when dealing with a circuit wired like this.
This outlet is commonly used for a heavy load such as a large air conditioner. The outlet should be wired to a dedicated 20-amp/240-volt circuit breaker in the service panel using 12|2 awg cable.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.