This drawing shows the wiring for multiple lights in a 4 way circuit with the source and fixtures coming before the switches. More lights can be added to this circuit by duplicating the wiring shown here for each additional fixture. Here 3-wire cable runs between L1 and L2, 2-wire cable runs from the last fixture to SW1, and 3-wires runs between SW1 and SW2.
The common terminals will always be connected to a hot wire, either from the source or on the light fixture. These connections can be reversed if it’s more convenient, as long as one of the 3 way common terminals connects to the hot source and the other one connects to the hot on the load, these circuits will work properly.
In this circuit a split receptacle is controlled by two separate switches. With this arrangement two lamps can be plugged into the same receptacle and each can be controlled separately from two different locations.
Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be connected to the switches in these circuits, although some smart switches may make use of a neutral wire to operate the device.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.