The 4 way comes right after the light fixture, but before the second 3 way switch, making it fall between the two 3 ways as needed. It could also be installed on the other side of the light and the effect would be the same.
In this circuit the source hot is at the common on the 3 way switch and 3-wire cable runs from there to the dimmer. The traveler wires run between the 2 switches and 2-wire cable runs from the dimmer to the light. The neutral from the source is spliced at each box to run through to the neutral terminal on the light fixture. The common on the dimmer is connected to the hot terminal on the light fixture.
The common terminals will always be connected to a hot wire, either from the source or on the light fixture. These connections can be reversed if it’s more convenient, as long as one of the 3 way common terminals connects to the hot source and the other one connects to the hot on the load, these circuits will work properly.
There are two sets of terminals on a ground fault circuit interrupter (gfci) receptacle: the line terminals and the load terminals. The source from the circuit should be connected to the line terminals and any standard duplex outlet or other device connected to the load terminals will be protected by this gfci.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.