Here the source is at the receptacle and 2-conductor cable runs from there to SW1. The hot source is spliced to a pigtail that connect to the bottom, always-hot, half on the receptacle and to the white cable wire which continues on to the bottom terminal on SW1. The black cable wire is connected to the top terminal on the split receptacle and runs to the top terminal on SW1. The circuit neutral wire is connected to one of the neutral terminals on the receptacle, it doesn’t run to the switch.
This is an older version of the receptacle in the first diagram. The slots are different sizes to accept polarized plugs, but it lacks a grounding slot. This device does not make use of a ground wire. There is no protection against electrocution as provide by the grounded receptacle.
This diagram illustrates the wiring for a split receptacle with the top half controlled by SW1 and the bottom half always hot. The receptacle is split by breaking the connecting tab between the two, brass colored terminals. The tab between the neutral, silver terminals should remain intact.
Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.